Conductors: bare, soft drawn, annealed copper per ASTM B-3, compact stranded
per ASTM B-496.
Strand shield: extruded semi-conducting compound.
Insulation: flame resistant (90℃) cross-linked polyethylene
(XLPE) ICEA S-75-381/NEMA WC-58.
Insulation shield: extruded semi-conducting compound. bare copper
tape helically applied.
Color code: Black, White, Red nylon tracer tape applied between the insulation
semi-conductive layer and the copper tape shield.
Ground wires: Uninsulated, soft drawn, annealed, compact stranded, bare copper
per ASTM B-496, B-8 and B-33.
Ground check: soft drawn, soft drawn, annealed, compact stranded, bare copper
with yellow EPR insulation.
Cabling: Three shielded conductors are assembled in a helical configuration with
two uninsulated ground wires, one yellow insulated ground check and non-wicking
fillers as needed .A woven nylon polyester reinforcement binder is served over the
entire assembly for increased stability.
Reinforcement: A woven nylon polyester reinforcement binder is applied over the
completed assembly for added core stability.
Jacket: Black flame retardant (90℃) PVC per ICEA S-75-381/NEMA WC-58.
Available in optional colors .